Monday, March 21, 2022 – Oceanside Area
POWER RESTORED AT 2:30 p.m.
Date: Monday, March 21, 2022
Location: Oceanside area.
Approximate Time Off: 1:05 p.m.
Estimated Time for Power Restoration: 3:00 p.m.
Cause: Failed cutout equipment.
Customers Affected: 740 customers initially, 321 customers out during repairs.
Status as of:
2:30 p.m.: Power has been restored to the area.
2:00 p.m.: A crew has isolated section of line that needs to be repaired and is making repairs to failed cutout equipment.
1:05 p.m.: A crew is responding.